New Hospital and New Medical Office Building
Electrical systems include nurse call; fire alarm; interior and exterior lighting; electrical distribution; security; lightning protection; data/telecommunication; and emergency back-up power.
The tele/datacommunication system consisted of complete design and specifications involving over 1700 Cat-6 cables; VoIP converged infrastructure; fiber optic backbone, wireless LAN infrastructure; patient monitoring; telecom room layouts; and computer room layouts.
The emergency back-up power system consists of two 1,000 kW generators.
Mechanical systems include HVAC, plumbing/piping, medical gas, and fire protection (completely sprinkled). The HVAC system was designed for five custom rooftop air handlers with variable frequency drives on supply and return fans and chilled water cooling coil; two rooftop air cooled chillers with packaged pump house, pre-piped/wired; three 125HP firebox hot water boilers (heating), two 125HP firebox boilers (sterilization, humidification, and domestic hot water); and a reverse osmosis system for boiler make-up. The air distribution consist of medium velocity supply mains; terminal units with heating coils; and ducted returns.
The hospital connects to a new 42,000 square foot medical office building. Connections include a data loop.